Control the Contactors with PLC
A typical application for contactor of DC operated is the direct control from the PLC. Hereby the contactor of a semiconductor output is supplied directly with control voltage. Typical semiconductor outputs of PLC’s provide a power of 500 mA at 24 Volts. Contactors up to 32 A can be operated directly by semiconductor output of this type without the additional coupler relays need.
The engineering cost of power DC supplies can be reduced by the use of electronics. The power supply no longer needs to be engineered as with conventional contactor coils according to the sum of the powers pick up. The power supply is engineered according to the considerations as following: the sums of the switch on powers of all contactors which pick up simultaneously are added to the sum of all holding the powers of all contactors which is switched on simultaneously. As the holding powers are very low the power supply can be smaller significantly.
The direct control of contactor coils from the PLC reduces the coupler relays costs and reduces the wiring effort involved. For this the output must provide both the holding and pick up power for the contactors coils. PLCs with different outputs are available on the market. There are also semi-conductor outputs are offered with 0.1 A or 0.5 A and the most common are the semi-conductor outputs with 500 mA, in addition to expensive relay outputs.
A significant difference between PLC’s for control of safe PLC’s and normal operational functions is the cyclic monitoring of the PLC outputs in safety PLC’s. The outputs of master drives are typically controlled and cyclically briefly interrupted in safety PLC’s. The interruption is in the order of just 10 – 5 ms, so that actuators of connected (valves, contactors) do not shut off. During the interruption it is monitored if the voltage of output drops below a defined level.
Posted by Cartiman Iman
♥ Favorite Labels ♥
- ► 2015 (130)
- ► 2014 (15)
- ► 2012 (274)
- ► 2011 (825)
- The Development Tools of CoDeSys
- Industrial Sectors and Interdependencies
- DeCoSys Development Utilizes PLCOpen and IEC 61131...
- Control Components of ICS
- ICS Control Systems for Critical Infrastructures
- The Security between ICS and IT
- Programming PLC with CoDeSys
- Assuring Industrial Control System Cyber Security
- PLC Program with easySoft CoDeSys
- Electric Power SCADA Systems
- Omron PLC for Serial Communication and Networks
- DynaStar DX Migration to Secure IP Routed Networki...
- Big Controller Features Scaled for Small Machine C...
- Weighing Machine Using PLC Mitsubishi
- GarretCom’s SCADA Frame Forwarding
- The Compact Controllers Package from Omron
- TOPKAPI Industrial SCADA Programming
- Control the Contactors with PLC
- OPC Server to Communicate with Communication Serve...
- Function Block Diagram PLC programming
- Relay Based SCADA
- Sequential Function Chart PLC Programming
- EtherMeter Standards based SCADA
- Security Approaches for Enhancing SCADA Security
- EtherMeter Eliminate Problem in Pulse Technology
- VT250 HMI Support CoDeSys
- Wonder Ware HMI Software
- Multi Function Display of HMI MFD4-5-XRC-30
- Vijeo Citect HMI Software
- The Family of Modicon from Schneider Electric
- High Level Standard of Modicon PLC
- Touch Screen HMI of VT250 from Turck
- G3 Series HMI for Multi Vendor Protocols
- HMI Development Using Adobe Flash Technologies
- Engineering Software of L-force Automation Machine...
- PLCopen Safety Function Blocks
- Human Factors in SCADA Systems
- The Quantum Safety PLC
- HMI Controller Program
- The Fundamental of Safety PLC
- Visual Basic as an HMI
- The Development Framework by PLCOpen
- The Major Components of HMIs
- The Fundamental Differences between Standard PLC a...
- Supervisory Level HMI
- Standards Certification of Safety PLC
- Industry Standard OPC Interface
- Simatic NET OPC Server
- OPC Data Access Automation
- SmartSymbol Wonderware InTouch
- Weighing Machine Using PLC Keyence
- Wireless Ethernet Bridges of Cirronet
- Advant Master DCS from ABB
- PLC Based Beam Dump Control
- General Windows Hardening Recommendations for OPC
- PLC Driver of DirectNet Software
- PLC Device Support Module
- Minimum Required Services of OPC
- Large Scale Distributed Control System
- Hardening Strategy for OPC Hosts
- Programming of DirectSOFT5 for PLCs
- OPC Protocol based on Microsoft Distributed Compon...
- The Design of SCADA System Challenges
- ▼ December 2010 (63)