GE Fanuc PLC Programming Software
In this article will explain about SoftPLC programming PLC that using GE Fanuc 90/30 I/O driver. It allows to access up to eight PCIF host I/O interface adapters. The driver consist 3 files, namely GE90/30.TLM, GECONFIG.EXE, and GE.LST. GE90/30.TLM is the runtime component, GECONFIG.EXE is a utility of displaying I/O information and generating an I/O report and GE.LST is the master configuration files.
When you install the SoftPLC you need to install GE90/30.TLM, GECONFIG.EXE and GE.LST under the \SPLCZ\IODVR\ directory. GE90/30.TLM is made known to SoftPLC by a line entry in the MODULE.LST file. Each I/O driver entry in MODULE.LST has to start with keyword “DRIVER”. Put the following line in the MODULE.LST file to be able to interface GE 90/30 I/O with SoftPLC:
DRIVER=C: \SPLCZ\IODVR\GE9030.TLM CFGFILE=C: \SPLCZ\IODVR\GE.LST
Here is the step by step to setting up the driver:
1. Edit the ‘Port’ column under the [CARDS] section of the GE.LST file for each of the card you will use. This normally resides in \SPLCZ\IODVR.
2. Set the switch settings on each card and install them in the host computer.
3. Attach the I/O racks, using a terminating resistor pack as might be needed on the last rack in each chain.
4. Insert the I/O modules and power up the racks.
5. Run the GECONFIG.EXE program from the \SPLCZ\IODVR directory and give it the name of your CFGFILE, which is normally GE.LST: C:>GEFONFIG GE>LST.
6. Press F3 to display all the communicating I/O module for each I/O network.
7. Press F4 to generate the GECARD.REP text file, which is a complete definition of how SoftPLC data table memory will be consumed for each I/O network.
8. Press F5 to generate default configuration file specification for each smart module.
9. Press F10 to exit GECONFIG.EXE.
10. Look at GECARD.REP and take note on how much data table memory you will need to allocate for each driver data type, for each I/O network.
11. Make the final edits to GE.LST, paying attention to the 5 xxWords columns for each I/O network.
Posted by Cartiman Iman
♥ Favorite Labels ♥
- ► 2015 (128)
- ► 2014 (15)
- ► 2012 (274)
- ► 2011 (825)
- GE Fanuc PLC Programming Software
- Push ON Push OFF With Data Memory PLC Omron
- MOV instruction on Omron PLC
- INC instruction on Omron plc
- EQU instructions on Omron PLC
- PLC Programming with RSLogix 5000
- Allen Bradley PLC Basics
- Programming PLC Watchdog Timer
- PLC Programming Standards
- Push ON Push OFF With Counter PLC Keyence
- Modicon PLC Programming
- PLC Operator Interface
- PLC Connection Diagram
- Fuzzy Logic Controller in PLC
- Fanuc PLC Programming
- Push ON Push OFF With Counter PLC Mitsubishi
- Function Block Diagram PLC
- PLC Flash Memory
- Difference between PLC and Microcontroller
- PLC with Touch Screen
- Push ON Push OFF With Counter PLC Omron
- PLC Inputs and Outputs
- PLC Analog Output
- Analog Input PLC
- Ladder Logic of Allen Bradley SLC 500
- Structural Monitoring Systems PLC Omron
- PLC Programming Structure
- Communication Monitoring InTouch - PLC
- PLC Thinget Low Cost and Reliable Solutions
- Push ON Push OFF With Internal Relay PLC Keyence
- PLC is Real-Time Applications
- Push ON Push OFF With Internal Relay PLC Mitsubish...
- OLE for Process Control (OPC) Introduction
- Push ON Push OFF With Internal Relay PLC Omron
- Serial Communication PLC Omron CPM1
- Elevator with PLC Program
- Interrupt Functions of PLC Omron CPM2A
- Elevator PLC Program with PLC Mitsubishi
- PAC is Hybrid of PLC and PC
- Elevator PLC Program with PLC Omron
- The Tasks of SCADA Software
- Introduction to System DCS DeltaV
- Elevator PLC Program with PLC Keyence
- How to Design SCADA System
- ▼ April 2010 (44)