**PLC Type KV, Name Input / Output PLC :**

**INPUT PLC :**

0000 ; Push Button Start

0001 ; Sensor1 Reverse

0002 ; Sensor1 Forward

0003 ; Sensor2 Reverse

0004 ; Sensor2 Forward

0005 ; Emergency Stop (Push Button)

**OUTPUT PLC :**

0500 ; Cylinder1 Forward

0501 ; Cylinder1 Reverse

0502 ; Cylinder2 Forward

0503 ; Cylinder2 Reverse

Download PDF File:

Keyence PLC for 3 movement(.pdf)

Please Download Programming for KV Builder :

**Keyence PLC Control for 3 movement**

Reading Ladder

**PLC Programming**for 3 movement with Standard Sequence Programming :

**1. INPUT CONDITION**

**a.**If 0005 = ON Then 1000 = ON

**b.**If 1000 = ON Then RES C000 or C000 = 0 (Only STEP0 = ON)

**c.**If 0001 = ON AND 0003 = ON Then 1001 = ON ( ALL ORIGIN = ON)

**d.**If 0000 = ON Then 1002 = ON (Start = ON)

**2. TRIGGER AND SENSOR CONDITION**

**a.**If 1100 = ON AND 1001 = ON AND 1002 = ON Then 1003 = ON AND 1101 = ON (STEP1 = ON)

**b.**If 1101 = ON AND 0002 = OFF Then 1003 = OFF AND Waiting STEP1

**c.**If 1101 = ON AND 0002 = ON Then 1003 = ON AND 1102 = ON (STEP2 = ON)

**d.**If 1102 = ON AND 0004 = OFF Then 1003 = OFF AND Waiting STEP2

**e.**If 1102 = ON AND 0004 = ON Then 1003 = ON AND 1103 = ON (STEP3 = ON)

**f.**If 1103 = ON AND 0001 = ON AND 0003 = ON Then 1100 = ON (STEP0 = ON) Else Waiting STEP3

**3. OUTPUT CONDITION**

**a.**If 1101 = ON Then 0500 = ON

**b.**If 1103 = ON Then 0501 = ON

**c.**If 1102 = ON Then 0502 = ON

**d.**If 1103 = ON Then 0503 = ON

**4. CONTROLLER**

**a.**If 1101 = OFF AND 1102 = OFF AND 1103 = OFF Then 1004 = ON (Only STEP0 = ON)

**b.**If 1004 = ON AND C000 Not Equal 0 (Null) Then RES C000 or C000 = 0 (Only STEP0 = ON)

**c.**If 1003 = ON (Trigger) Then Count Up C000

**d.**If 1000 = ON (Emergency Stop) Then RES C000 or C000 = 0 (Only STEP0 = ON)

**e.**If C000 = 0 Then 1100 = ON (STEP0 = ON)

**f.**If C000 = 1 Then 1101 = ON (STEP1 = ON)

**g.**If C000 = 2 Then 1102 = ON (STEP2 = ON)

**h.**If C000 = 3 Then 1103 = ON (STEP3 = ON)

**Keyence PLC programming for Control 3 movement**

with Standard Sequence Programming

with Standard Sequence Programming

Back to :

**PLC Control for 3 movement**